||Supply and Installation of DG set
||od867/2019_2020 : Supply, Conveyance, Unloading, Lifting and placing in position, Testing and commissioning of 82.5 KVA, 3 phase, 415 V Diesel Generator Set with Integral Acoustic Enclosure as per CPCB Norms with standard accessories including self starting arrangements, standard control panel etc. complete as per technical details given below.1. Make of Engine - KOEL/Cummins/Volvo/Cooper/Greaves, No. of Cylinders as per manufactures standards, Water cooled, Radiator with fan provided with fan guard, fuel pump, fuel filter, Exhaust silencer, Muffler, Battery Charger/Generator, Engine instrument panel with starting switch with key or button, Oil pressure and water temperature gauges etc. complete.2. Alternator - kirlosker/KEL/Crompton/Stamford/Greeves self exited and self regulated 82.5 KVA, 3 Phase, 415 Volts, 50 Hz.Fuel tank suitable size built in type integrated with the acoustic enclosure, Battery suitable size built in type integrated battery with leads and terminals of appropriate AH capacity. etc. complete.
||Allied Electrification work
||od868/2019_2020 : Supply and installation of 4 pole, 415V, 125A On load Change Over Switch in suitable sheet steel enclosure including connection.
||od1293/2020_2021 : Fabrication, Supply and fixing Cubicle type MS Box of size 350 x 300 x 200 mm made out of 16 gauge sheet for fixing MCCB / TPN SDF Unit. with hinges for operating the door including locking arrangements neatly painted as per specifications and directions of the departmental officers.
||2.1.5 : Providing and fixing following capacity TP&N disconnector fuse switch unit inside the existing panel board with ISI marked HRC fuses including drilling holes in cubicle panel, making connections, etc. as required.160 Amp TP&N
||188.8.131.52 : Supply & laying of one number PVC insulated and PVC sheathed armoured aluminium power cable of 1.1KV grade of the following sizes in ground including excavation of trench of size 35 x 75 cm, refilling the trench etc. as required but excluding sand cushioning and protective covering (in ordinary soil).3.5 core 95 sq mm
||184.108.40.206 : Supply, laying and clamping of 1 no. PVC insulated and PVC sheathed armoured aluminium power cable, 1.1 KV grade of the following sizes using clamps noted along with the cables, spacing of clamps not exceeding 60cms, making good the damages , colour washing etc. as required.3.5 core 95 sq mm
||9.1.24 : Supplying and making end termination with brass compression gland and aluminium lugs for \nfollowing size of PVC insulated and PVC sheathed / XLPE aluminium conductor cable of 1.1 KV \ngrade as required.3 1/2X 95 sq. mm (45mm)
||5.4 : Earthing with G.I. earth plate 600 mm X 600 mm X 6 mm thick including accessories, andproviding masonry enclosure with cover plate having locking arrangement and watering pipe of 2.7 metre long etc. with charcoal/ coke and salt as required.
||5.8 : Supplying and laying 25 mm X 5 mm copper strip at 0.50 metre below ground as strip earthelectrode, including connection/ terminating with nut, bolt, spring, washer etc. as required.(Jointing shall be done by overlapping and with 2 sets of brass nut bolt & spring washer spaced at 50mm)
||220.127.116.11 : Supply and drawing bare earthing conductors of the following sizes along with wiring/ cables and giving connection as required2.00 mm copper conductor ( 14 SWG)
||18.104.22.168 : Supply and drawing bare earthing conductors of the following sizes along with wiring/ cables and giving connection as required3.15 mm copper conductor ( 10 SWG)
||22.214.171.124 : Supply and drawing bare earthing conductors of the following sizes along with wiring/ cables and giving connection as required4.00 mm copper conductor ( 8 SWG)
||126.96.36.199 : Supply and drawing bare earthing conductors of the following sizes along with wiring/ cables and giving connection as required6.00 mm copper conductor (4 SWG)
||14.11 : Providing brick work (in width 225 mm or more) with F.P.S. bricks of class designation 7.5 in cement mortar 1:4 (1 cement : 4 coarse sand) at all levels.
||14.8 : Providing and laying in position cement concrete 1 :3:6 (1 cement : 3 coarse sand : 6 graded stone aggregate 20 mm nominal size) in foundation of pump, DG set etc. including form work etc. as required.
||14.12.1 : Providing 15mm thick cement plaster of mix 1:4 (1 cement : 4 fine sand) at all levels.